Store at: 0 to +50 °C
Install at: 0 to +50 °C, Bend minimum: 16 times V.D.
Operate at: -20 to +90 °C, Bend minimum: 16 times V.D.
Conductor material: stranded plain copper conductor according to IEC60228 Cl.2, 0,50mmq (7×0,30mm)
Insulation: PVC extruded compound
Lay up: cores stranded into pairs. Colors: red, white,
Single screen: on each pair polyester tape + aluminium/mylar tape 100% coverage and 25% overlap with metal side in contact with a tinned copper drain wire 7×0,30 size 0,5sqmm, and over the screen a further mylar tape.
Assembly: triads twisted in bundle
Overall screen: aluminium/mylar tape 100% coverage with 25% overlap with metal side in contact with a tinned drain wire 7×0,30.
Outer Sheath: special PVC Low Smoke and Fume extruded compound
Marking: APS Finland – ww/yy – FIRE RETARDANT CONTROL CABLE RE4XHOHR n°x2x0.50 – 300/500V – PVC +90°C – IEC60332-3-24 – P/N – lot + meter
Environmental properties and Fire Performances
Flame retardant: IEC60332-3-24, CEI 20-22/3
HCL emission: <= 22%
Hydrocarbon and UV resistant:
Max operating Voltage: 500V
Inductance: max 1.25 mH/Km
Capacitance: <= 150 nF/Km @ 1KHz
Conductor resistance: 24,5 ohm/Km ( + 5% for multicores)
Test voltage core to core: 2 Kv
Ordering and delivery information
|Type||P/N||Nom. O.D [mm]||Nom. weight [kg/km]||Packaging|
|4 x 2 x 0.50 sqmm||CURR21C0004||13 mm||250||500m (+/-5%)|
|12 x 2 x 0.50 sqmm||CURR21C0005||20 mm||540||500m (+/-5%)|
Every effort has been put so that this document is most reliable and free from errors. However, AP Solutions Oy cannot be considered responsible for any mistake in this document and users should consult AP Solutions Oy for any information needed. AP Solutions Oy reserves the right to make changes to the documents at any time, without prior notice.